EWLD110J-SS | EWLD130J-SS | EWLD145J-SS | EWLD165J-SS | EWLD235J-SS | EWLD195J-SS | EWLD265J-SS | EWLD290J-SS (Archived) | EWLD310J-SS (Archived) | EWLD330J-SS (Archived) | EWLD360J-SS (Archived) | EWLD390J-SS (Archived) | EWLD430J-SS (Archived) | EWLD470J-SS (Archived) | EWLD500J-SS (Archived) | EWLD530J-SS (Archived) | |||||
---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|

Cooling capacity | Nom. | kW | 110 (1) | 128 (1) | 142 (1) | 163 (1) | 236 (1) | 191 (1) | 264 (1) | 285 (1) | 306 (1) | 327 (1) | 355 (1) | 382 (1) | 428 (1) | 473 (1) | 501 (1) | 529 (1) | ||

Capacity control | Method | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | |||

Minimum capacity | % | 25.0 | 25.0 | 25.0 | 25.0 | 25.0 | 25.0 | 25.0 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | |||

Power input | Cooling | Nom. | kW | 31.2 (1) | 38.4 (1) | 43.8 (1) | 50.4 (1) | 66.0 (1) | 56.0 (1) | 75.3 (1) | 87.4 (1) | 94.0 (1) | 100 (1) | 106 (1) | 111 (1) | 122 (1) | 132 (1) | 141 (1) | 150 (1) | |

EER | 3.51 (1) | 3.33 (1) | 3.25 (1) | 3.24 (1) | 3.58 (1) | 3.42 (1) | 3.51 (1) | 3.26 (1) | 3.25 (1) | 3.25 (1) | 3.35 (1) | 3.43 (1) | 3.52 (1) | 3.59 (1) | 3.55 (1) | 3.52 (1) | ||||

Dimensions | Unit | Height | Mm | 1,020 | 1,020 | 1,020 | 1,020 | 1,020 | 1,020 | 1,020 | 2,000 | 2,000 | 2,000 | 2,000 | 2,000 | 2,000 | 2,000 | 2,000 | 2,000 | |

Width | Mm | 913 | 913 | 913 | 913 | 913 | 913 | 913 | 913 | 913 | 913 | 913 | 913 | 913 | 913 | 913 | 913 | |||

Depth | Mm | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | 2,684 | |||

Weight | Unit | kg | 1,124 | 1,141 | 1,237 | 1,263 | 1,489 | 1,305 | 1,489 | 2,474 | 2,500 | 2,526 | 2,568 | 2,611 | 2,795 | 2,979 | 2,979 | 2,979 | ||

Operation weight | kg | 1,138 | 1,159 | 1,253 | 1,281 | 1,518 | 1,327 | 1,518 | 2,505 | 2,533 | 2,562 | 2,608 | 2,655 | 2,845 | 3,036 | 3,036 | 3,036 | |||

Water heat exchanger - evaporator | Type | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | |||

Compressor | Type | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | |||

Quantity | 1 | 1 | 1 | 1 | 1 | 1 | 1 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | ||||

Sound power level | Cooling | Nom. | dBA | 89 | 89 | 89 | 89 | 89 | 89 | 89 | 94 | 94 | 94 | 94 | 94 | 94 | 94 | 94 | 96 | |

Sound pressure level | Cooling | Nom. | dBA | 79 (2) | 79 (2) | 79 (2) | 79 (2) | 79 (2) | 79 (2) | 79 (2) | 82 (2) | 82 (2) | 82 (2) | 82 (2) | 82 (2) | 82 (2) | 82 (2) | 82 (2) | 83 (2) | |

Operation range | Evaporator | Cooling | Min. | °CDB | -10 | -10 | -10 | -10 | -10 | -10 | -10 | -10 | -10 | |||||||

Max. | °CDB | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | ||||||||||

Condenser | Cooling | Min. | °CDB | 25 | 25 | 25 | 25 | 25 | 25 | 25 | 25 | 25 | ||||||||

Max. | °CDB | 60 | 60 | 60 | 60 | 60 | 60 | 60 | 60 | 60 | ||||||||||

Refrigerant | Type | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | |||

GWP | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | ||||

Circuits | Quantity | 1 | 1 | 1 | 1 | 1 | 1 | 1 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | |||

Piping connections | Discharge line connection | inch | 2"1/2 | 4" | 4" | 4" | 4" | 4" | 4" | 4" | 4" | 4" | 4" | 4" | 4" | 4" | 4" | 4" | ||

Power supply | Phase | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | |||

Frequency | Hz | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | |||

Voltage | V | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | |||

Notes | (1) - Cooling: entering evaporator water temp. 12.0°C; leaving evaporator water temp. 7.0°C; condensing temperature 45.0°C, unit at full load operation. | (1) - Cooling: entering evaporator water temp. 12.0°C; leaving evaporator water temp. 7.0°C; condensing temperature 45.0°C, unit at full load operation. | (1) - Cooling: entering evaporator water temp. 12.0°C; leaving evaporator water temp. 7.0°C; condensing temperature 45.0°C, unit at full load operation. | |||||||||||||||||

(2) - Sound level data are measured at entering evaporator water temp. 12.0°C; leaving evaporator water temp. 7.0°C; condensing temperature 45.0°C; full load operation; standard: ISO3744. | (2) - Sound level data are measured at entering evaporator water temp. 12.0°C; leaving evaporator water temp. 7.0°C; condensing temperature 45.0°C; full load operation; standard: ISO3744. | (2) - Sound level data are measured at entering evaporator water temp. 12.0°C; leaving evaporator water temp. 7.0°C; condensing temperature 45.0°C; full load operation; standard: ISO3744. | ||||||||||||||||||

(3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | (3) - Fluid: Water | |||||

(4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (4) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | |||||

(5) - Maximum starting current: starting current of biggest compressor + current of the other compressor at 75 % of maximum load | (5) - Maximum starting current: starting current of biggest compressor + current of the other compressor at 75 % of maximum load | (5) - Maximum starting current: starting current of biggest compressor + current of the other compressor at 75 % of maximum load | ||||||||||||||||||

(6) - Nominal current cooling mode is referred to the following conditions: evaporator 12/7°C; condenser 30/35°C; compressors current | (6) - Nominal current cooling mode is referred to the following conditions: evaporator 12/7°C; condenser 30/35°C; compressors current | (6) - Nominal current cooling mode is referred to the following conditions: evaporator 12/7°C; condenser 30/35°C; compressors current | ||||||||||||||||||

(7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | (7) - Maximum running current is based on max compressor absorbed current in its envelope | |||||

(8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (8) - Maximum unit current for wires sizing is based on minimum allowed voltage. | |||||

(9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | (9) - Maximum current for wires sizing: compressor full load ampere x 1.1 | |||||

(10) - For more details on the operating limits please refer to the Chiller Selection Software (CSS). | (10) - For more details on the operating limits please refer to the Chiller Selection Software (CSS). | (10) - For more details on the operating limits please refer to the Chiller Selection Software (CSS). | ||||||||||||||||||

(11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases | (11) - Its functioning relies on fluorinated greenhouse gases |