EWAD200D-HS | EWAD210D-HS | EWAD230D-HS | EWAD260D-HS | EWAD270D-HS | EWAD290D-HS | EWAD310D-HS | EWAD340D-HS | EWAD380D-HS | EWAD420D-HS | EWAD450D-HS | EWAD480D-HS | EWAD510D-HS | EWAD550D-HS | EWAD590D-HS | |||||
---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|

Cooling capacity | Nom. | kW | 194 (1) | 208 (1) | 233 (1) | 255 (1) | 272 (1) | 288 (1) | 305 (1) | 334 (1) | 379 (1) | 413 (1) | 446 (1) | 476 (1) | 512 (1) | 545 (1) | 585 (1) | ||

Capacity control | Method | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | Stepless | |||

Minimum capacity | % | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | 12.5 | |||

Power input | Cooling | Nom. | kW | 77.9 (1) | 76.0 (1) | 83.9 (1) | 92.1 (1) | 98.9 (1) | 105 (1) | 114 (1) | 122 (1) | 129 (1) | 143 (1) | 152 (1) | 164 (1) | 177 (1) | 185 (1) | 194 (1) | |

EER | 2.49 (1) | 2.73 (1) | 2.77 (1) | 2.77 (1) | 2.75 (1) | 2.73 (1) | 2.68 (1) | 2.75 (1) | 2.93 (1) | 2.90 (1) | 2.93 (1) | 2.90 (1) | 2.89 (1) | 2.95 (1) | 3.02 (1) | ||||

ESEER | 3.02 | 3.16 | 3.24 | 3.11 | 3.20 | 3.18 | 3.17 | 3.15 | 3.46 | 3.50 | 3.57 | 3.57 | 3.55 | 3.60 | 3.68 | ||||

Dimensions | Unit | Depth | mm | 2,239 | 2,239 | 3,339 | 3,339 | 3,339 | 3,339 | 3,339 | 4,040 | 4,040 | 4,040 | 4,040 | 4,940 | 4,940 | 4,940 | 4,940 | |

Height | mm | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | 2,223 | |||

Width | mm | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | 2,234 | |||

Weight | Operation weight | kg | 2,500 | 2,500 | 2,960 | 2,960 | 2,960 | 2,960 | 2,960 | 3,300 | 3,300 | 3,447 | 4,112 | 4,526 | 4,526 | 4,526 | 4,526 | ||

Unit | kg | 2,475 | 2,470 | 2,865 | 2,865 | 2,870 | 2,870 | 2,870 | 3,185 | 3,185 | 3,277 | 3,942 | 4,356 | 4,361 | 4,361 | 4,366 | |||

Water heat exchanger | Type | Plate heat exchanger | Plate heat exchanger | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | Single pass shell & tube | |||

Water volume | l | 25 | 30 | 95 | 95 | 90 | 90 | 90 | 115 | 115 | 170 | 170 | 170 | 165 | 165 | 160 | |||

Air heat exchanger | Type | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | |||

Fan | Air flow rate | Nom. | l/s | 21,848 | 21,153 | 32,772 | 32,772 | 32,251 | 31,729 | 31,729 | 43,696 | 43,696 | 43,696 | 42,306 | 54,620 | 54,620 | 54,620 | 54,620 | |

Fan motor | Speed | Cooling | Nom. | rpm | 890 | 890 | 890 | 890 | 890 | 890 | 890 | 890 | 890 | 890 | 890 | 890 | 890 | 890 | 890 |

Compressor | Quantity | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | |||

Type | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | Asymmetric single screw compressor | ||||

Operation range | Air side | Cooling | Max. | °CDB | 48 | 48 | 48 | 48 | 48 | 48 | 48 | 48 | 48 | 48 | 48 | 48 | 48 | 48 | 48 |

Min. | °CDB | -18 | -18 | -18 | -18 | -18 | -18 | -18 | -18 | -18 | -18 | -18 | -18 | -18 | -18 | -18 | |||

Water side | Cooling | Max. | °CDB | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | 15 | |

Min. | °CDB | -15 | -15 | -15 | -15 | -15 | -15 | -15 | -15 | -15 | -15 | -15 | -15 | -15 | -15 | -15 | |||

Sound power level | Cooling | Nom. | dBA | 96 | 96 | 96 | 96 | 96 | 96 | 96 | 97 | 99 | 97 | 98 | 98 | 98 | 99 | 100 | |

Sound pressure level | Cooling | Nom. | dBA | 77 (2) | 77 (2) | 77 (2) | 77 (2) | 77 (2) | 77 (2) | 77 (2) | 77 (2) | 79 (2) | 77 (2) | 78 (2) | 78 (2) | 78 (2) | 79 (2) | 80 (2) | |

Refrigerant | Type | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | R-134a | |||

GWP | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | 1,430 | ||||

Circuits | Quantity | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | |||

Charge | Per circuit | kg | 18.0 | 21.0 | 22.0 | 26.0 | 28.0 | 31.0 | 28.0 | 28.0 | 34.0 | 30.0 | 45.0 | 47.5 | 46.0 | 46.0 | 47.0 | ||

Per circuit | TCO2Eq | 25.7 | 30.0 | 31.5 | 37.2 | 40.0 | 44.3 | 40.0 | 40.0 | 48.6 | 42.9 | 64.4 | 67.9 | 65.8 | 65.8 | 67.2 | |||

Power supply | Phase | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | |||

Frequency | Hz | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | |||

Voltage | V | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | |||

Compressor | Starting method | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | Wye-Delta | |||

Notes | Cooling: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation. | Cooling: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation. | Cooling: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation. | ||||||||||||||||

Sound pressure levels are measured at entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation; Standard: ISO3744 | Sound pressure levels are measured at entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation; Standard: ISO3744 | Sound pressure levels are measured at entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation; Standard: ISO3744 | |||||||||||||||||

Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | |||||

Maximum starting current: starting current of biggest compressor + 75 % of maximum current of the other compressor + fans current for the circuit at 75 % | Maximum starting current: starting current of biggest compressor + 75 % of maximum current of the other compressor + fans current for the circuit at 75 % | Maximum starting current: starting current of biggest compressor + 75 % of maximum current of the other compressor + fans current for the circuit at 75 % | |||||||||||||||||

Nominal current in cooling mode: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C. Compressor + fans current. | Nominal current in cooling mode: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C. Compressor + fans current. | Nominal current in cooling mode: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C. Compressor + fans current. | |||||||||||||||||

Maximum running current is based on max compressor absorbed current in its envelope and max fans absorbed current | Maximum running current is based on max compressor absorbed current in its envelope and max fans absorbed current | Maximum running current is based on max compressor absorbed current in its envelope and max fans absorbed current | |||||||||||||||||

Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | Maximum unit current for wires sizing is based on minimum allowed voltage. | |||||

Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | |||||

Equipment contains fluorinated greenhouse gases. Actual refrigerant charge depends on the final unit construction, details can be found on the unit labels. | Equipment contains fluorinated greenhouse gases. Actual refrigerant charge depends on the final unit construction, details can be found on the unit labels. | Equipment contains fluorinated greenhouse gases. Actual refrigerant charge depends on the final unit construction, details can be found on the unit labels. |